To help you make difficult easy, Fibox has prepared copy and past text for adding Fibox non-metallic NEMA 4X enclosures your project document (or download a pdf version for your files).
If you have any questions, please feel free to contact Fibox customer service for more information.
FIBOX – ARCA JIC HINGED COVER NONMETALLIC ENCLOSURES – PRODUCT SPECIFICATIONS
A. Comply with UL 50, “Cabinets and enclosures” and NEMA Type 1, 3, 3s, 4, 4x, 6, 6p, 12, and 13.
B. Construction: Polycarbonate/Plastic
C. Body shall be manufactured from a high-impact, corrosion resistant material; UV stabilized for outdoor use, and comply with UL-94 minimum V-0 requirements.
D. Cover shall be manufactured from a high-impact, corrosion-resistant material, UV stabilized for outdoor use, and comply with UL-94 minimum V-0 requirements.
E. Body and cover shall maintain physical properties through an overall long term temperature range of -40° F to 175°F and short term temperature range of -40°F to 284°F.
F. Body and cover shall be free of rough corners, sharp edges or burrs.
G. Cover screws (10-32) shall be captive with a slotted stainless steel (type 304) fillister head.
H. Door: Continuous hinge; stainless steel lockable latch unless otherwise indicated, formed-in-place (FIP) gasket.
I. Mounting Panel: Provide painted removable internal mounting panel for component installation.
J. 10-32 or ¼-20(depending on size) brass threaded inserts for mounting panel & mounting feet.
K. Mounting feet shall be removable.
L. Back panel mounting means shall accept standard size back panels.
M. Nonmetallic enclosures shall be listed and labeled as defined in UL 50, by a qualified testing agency, and marked for intended location and application.